- Research article
- Open Access
Wastewater treatment using integrated anaerobic baffled reactor and Bio-rack wetland planted with Phragmites sp. and Typha sp.
© Jamshidi et al.; licensee BioMed Central Ltd. 2014
- Received: 14 January 2014
- Accepted: 15 October 2014
- Published: 25 October 2014
The purpose of this study is to examine the potential use of anaerobic baffled reactor (ABR) followed by Bio-rack wetland planted with Phragmites sp. and Typha sp. for treating domestic wastewater generated by small communities (751 mg COD/L, 500 SCOD mg/L, 348 mg BOD5/L). Two parallel laboratory-scale models showed that the process planted with Phragmites sp. and Typha sp. are capable of removing COD by 87% & 86%, SCOD by 90% & 88%, BOD5 by 93% & 92%, TSS by 88% & 86%, TN by 79% & 77%, PO4-P by 21% & 14% at an overall HRT of 21 (843 g COD/m3/day & 392 g BOD5/m3/day) and 27 (622 g COD/m3/day & 302 g BOD5/m3/day) hours, respectively. Microbial analysis indicated a high reduction in the MPN of total coliform and TVC as high as 99% at the outlet end of the processes. The vegetated system using Phragmites sp. showed significantly greater (p <0.05) pollutant removal efficiencies due to its extensive root and mass growth rate (p <0.05) of the plant compared to Typha sp. The Phragmites sp. indicated a higher relative growth rate (3.92%) than Typha sp. (0.90%). Microorganisms immobilized on the surface of the Bio-rack media (mean TVC: 2.33 × 107 cfu/cm2) were isolated, identified and observed using scanning electron microscopy (SEM). This study illustrated that the present integrated processes could be an ideal approach for promoting a sustainable decentralization, however, Phragmites sp. would be more efficient rather than Typha sp.
- Anaerobic baffled reactor
- Bio-rack wetland system
- Phragmites sp
- Typha sp
- Domestic wastewater treatment
Decentralized wastewater treatment systems (DEWATS) are appropriate for low-density communities and varying site conditions, and are more cost-effective than centralized practices. However, the efficiency of these systems depends on the attributes, and design criteria of the selected process . Therefore, it is imperative to conduct research in order to develop a feasible and sustainable treatment technique for decentralization.
Anaerobic baffled reactor (ABR) reported to be a promising solution in domestic wastewater treatment -. The system recognized by incorporating the advantages of upflow anaerobic sludge blanket (UASB) and phase separation. It consists of alternating hanging and standing baffles, which compartmentalizes the reactor . This practice leads the flow into intimate contact with the biomass ,, resulting in partial separation of acidogenesis and methanogenesis longitudinally down the reactor, and more stable operation -. It has been shown to provide higher resilience to hydraulic and organic shock loads, higher treatment rate, longer biomass retention times, and lower sludge yields than other anaerobic treatment systems . Previous hydrodynamic studies revealed that the low dead space (7% to 30%) occurred in ABR . Nasr et al.  reported removal efficiencies of 76% for total chemical oxygen demand (COD), and 55% for biochemical oxygen demand (BOD5) in ABR treating domestic wastewater at a hydraulic retention time (HRT) of 12 hours. Bodkhe  used a modified ABR in order to achieve 84% COD, and 87% BOD5 in treating municipal wastewater at a HRT of 6 hours. Feng et al.  used a bamboo carrier ABR to treat sewage achieving 69% COD reduction at a HRT of 18 hours. Despite the significant advantages and efforts made worldwide, typically the effluent of ABR technique is totally nutrients rich, oxygen deficit, and containing high concentration of unacceptable pathogen . This would surely deteriorate the quality of surface waters in rural areas. In fact, it requires post treatment for removing the remaining organic matters, nutrients and pathogens.
In the recent years, the application of constructed wetlands for wastewater treatment has received greater attention since they offer a cost effective and an environmentally sound approach . In that order, the possible applications of integrated anaerobic pretreated-constructed wetlands have been introduced as a promising model for DEWATS -. The major mechanism associated in constructed wetland for pollutant removal is the interaction between the bacterial metabolism and plant uptake, respectively, termed as rhizoremediation and phytoextraction . Plants transfer oxygen to their root system and release a fraction of this oxygen into the rhizosphere for aerobic bacterial activity . The type of aquatic plant species can also act as an important biotic factor in the treatment efficiency of constructed wetlands . In that order, among various aquatic weeds, Phragmites sp. and Typha sp. are two well-known macrophytes demonstrated as potentially valuable vegetation in the natural purification process . Nevertheless, the use of constructed wetlands, either as a standalone or combined solution, could be restricted by choking, clogging, slow mass transfer, poor root penetration into the multilayer soil column, high area requirement and capital investment. It is implied that conventional decentralized treatment processes are required to be optimized and upgraded to prevail over the limitations.
In our earlier recent work, the application of ABR has been studied comprehensively to optimize its design and operation in pollutant removal from domestic wastewater (~350-750 mg COD/L), and it was simulated by artificial neural network ,. On the other hand, the Bio-rack system (BRS) is one of the latest evolutions of wetland technologies that developed to overcome the drawbacks of conventional wetland processes . This is a robust biological practice that can be applied to the efficient and reliable elimination of pollutants, even under unfavorable influent conditions stressed by high total dissolved solids and heavy metal ,. Analytical data which collected during the treatment of domestic wastewater (COD ≤440 mg/L, BOD5 ≤ 238 mg/L) showed that this process able to reduce up to 80% COD, and 90% BOD5 at a HRT of 10 hours . The process is designed by incorporating the advantages of engineered attached growth (using a support matrix of the Bio-racks) and phytoremediation systems. The Bio-rack technique provides a desirable condition for plant root growth, efficient oxygen diffusion, and a distinguished surface area for a superior microbial population responsible for organic degradation at much low area requirement and capital cost . The interrelationships between the plants and microorganisms associated with biofilms attached to the racks, stems, roots, and water column form a high rate wetland system. A further study also revealed the efficiency of this method planted with Thalia dealbata, Acorus calamus, Zizania latifolia and Iris sibirica for river water treatment ,. Marchand et al.  successfully applied a Bio-racks filled with a homogeneous mix of gravels and perlite for the removal of copper ion from synthetic Cu-contaminated wastewaters using Phragmites australis, Juncus articulatus and Phalaris arundinacea.
Hence, it is recommended that using Bio-rack wetland upgraded with ABR should be considered as a novel scientific advancement and integrated approach. This innovation has not been documented before; its performance would be controversial and requires to be optimized thoroughly. This study is aimed to develop and examine the performance of an integrated process of ABR and BRS for effective treatment of domestic wastewater which could be implemented in decentralization practices. The potential ability of two aquatic plants, included Phragmites sp. and Typha sp., in wetland phytoremediation were also compared to find the most efficient and well matched vegetation in the combined ABR and BRS. This is important to have a comparative assessment on the use of aquatic weeds in the phytoremediation systems, where the most suitable macrophytes are available.
The characteristic of wastewater
The overall characteristic of domestic wastewater during the study period was as follows: pH 7.44 × 0.12, total chemical oxygen demand (COD) 751 × 43 mg/L, soluble chemical oxygen demand (SCOD) 500 × 45 mg/L, biochemical oxygen demand (BOD5) 348 × 26 mg/L, dissolved oxygen (DO) 0.19 × 0.07 mg/L, total suspended solids (TSS) 528 × 41 mg/L, total nitrogen (TN) 64.65 × 5.14 mg/L, phosphate (PO4-P) 13.7 × 1 mg/L, total coliform 5.27 × 107 × 1.8 × 107 MPN/100ml, and total viable count (TVC) 3.30 × 107 × 6.53 × 106cfu/ml.
Chemicals and instrumentation
The chemicals used in this study were of analytical grade (from Merck, Germany) as follows: Borax, Bromocresol green (5%), Citric acid, Ferroin indicator, Formaldehyde solution, Methyl red (1%), Starch, Ag2SO4, CaCl2, C20H14O4, C2H5OH, CuSO4.5H2O, FeCl3.6H2O, Fe(NH4)2(SO4)2.6H2O, H3BO3, HCl, HgSO4, H2SO4, K2Cr2O7, KI, KH2PO4, K2HPO4, K2SO4, MnSO4.4H2O, NaCl, NaHCO3, NaN3, NaOH, Na2SO4, Na2S2O3.5H2O, Na2HPO4.7H2O, Na2S2O3.5H2O, (NH4)6Mo7O24.4H2O, (NH4)2S2O8, NH4Cl, MgSO4.7H2O, Nutrient agar, and MacConkey broth.
The sample pH was measured by a pH-meter model 75P (Istek, Korea). COD tests were performed by using the open-reflux digestor model EME6/CEB (Electrothermal, UK). TN was examined via the semimicro Kjeldahl setup. UV-visible spectrophotometer model P/N BUV40X00 (PerkinElmer, USA) was used to measure PO4-P. Steroscan 440 scanning electron microscope (SEM, Leica, Cambridge, UK) was used during observation of active biomass on the support matrix (Bio-rack).
Pilot plant setup
Each Plexiglas anaerobic baffled reactor (Length: 0.94 m, Width: 0.16 m, Height: 0.5 m) with 60 L net volume, consists of equally six compartments. The compartments were arranged by further vertical baffles dividing upflow-to-downflow parts by a ratio of 3:1 to affect the fluid dynamics in the sludge bed . In this process, the wastewater force to flow under and over the baffles from one compartment to the next as it passes from the inlet to the outlet. The biogas formed during the anaerobic fermentation was released by the exhaust valves located on the top of the reactor.
The wetland systems (Bio-rack units) included a rectangular tank measuring 0.32 m × 0.3 m × 0.6 m (L × W × H), an effective depth of 0.54 m, and a 50 L void volume in the presence of vegetation and other internals. Unique feature of this system is the presence of 15 vertical PVC pipes (a 500 mm effective height × 60 mm outer diameter), free of soil strata, assembled as a rack and called Bio-rack. The pipes contained numerous surface perforations (20 mm diameter) for liquid transportation. These Bio-racks are involved in the treatment process by holding vegetation and providing an abundant attachment site for microbial growth. In this practice, the wastewater is distributed uniformly and then flows horizontally through the support matrix (Bio-racks), stems and roots of the plants to treat by physical and biological processes. The occupied area and specific surface of the matrix Bio-rack were 0.06 m2 and 55 m2/m3 effective volume (57 m2/m3 filled volume), respectively. Sixty Phragmites sp. and thirty Typha sp. plants were held in the support matrix of the Bio-rack at the initial stage of the plantation. The lower number of Typha sp. was used because these plans are larger in size compared to Phragmites sp. The inlet and outlet arrangements were made as per standard practices.
Start-up and acclimatization
The experiments were initiated with the batch mode of merely anaerobic baffled reactors by seeding the mixture of cow dung and sewage sludge at the ratio of 1:2 (50% v/V) on effluent wastewater in each compartment for 2 weeks. The content of the reactors was recycled for homogeneity in the same period. Subsequently, the two comparable anaerobic baffled reactors in combination with Bio-rack systems were operated through serial exposure of sewage starting from 25% loading rate, which was increased gradually to 100% at an overall HRT of 44 hours over a 25 day period. In this stage, the systems continued to perform for more 45 days until the reduction in the percentage of COD reached a constant level, which was considered as the acclimatization period. Initially, the plant density was low and gradually the plant growth and reached their maximum possible number as bacterial growth was enhanced. In that order, the ratio of the volatile fatty acids to total alkalinity concentration was observed to be maintained below 0.3 at the outlet end of the ABR during studies.
It is noteworthy to say that the Phragmites sp. and Typha sp. were obtained from marshy lands of Tehran Province and Malayer County, respectively. Sampling was accomplished with simple hand tools. The underground parts (roots and bulbs) of the plants were carefully dug up, and the soil removed with care. A plastic collection container containing water marsh was used for transferring the sampled plants and minimizing their damage through several mechanisms. In the lab, the roots of sampled plants were washed with tap water to remove any remaining adsorbed soil particles before preliminary plantation. The type of the plants determined with the help of the National Botanical Garden, Teharan, Iran.
Experimental conditions implied in wastewater treatment
Operation period (day)
Overall HRT (hours)
50 × 2.63
61 × 3.02
68 × 2.02
85 × 6.02
93 × 6.46
113 × 2.56
23 × 1.96
29 × 2.60
33 × 2.09
40 × 3.51
43 × 3.07
50 × 4.11
455 × 24
553 × 27
622 × 18
769 × 55
843 × 59
1024 × 23
205 × 18
260 × 24
302 × 19
361 × 32
392 × 28
452 × 37
where V (L) is the void volume of the reactor, and Q (L/hour) is the design flow rate. Wastewater flow (L/day) expresses the design wastewater flow over a 24 hour period. Overall HRT indicates the sum of retention time both ABR and wetland system.
The inflow rates were fixed accordingly to 65, 80, 96, 114, 126 and 144 L/day for overall HRTs of 41, 33, 27, 23, 21 and 18 hours, respectively. The systems are operated at each retention time for 60 days, during which the effluent characteristics with an almost constant percentage reduction were achieved.
Additionally, the old plants were removed periodically and new plants were retained or allowed to grow during experimentations. In general, the roots of young plants can display greater ability to absorb impurities and release oxygen than old plants due to the age of the plants and tissues. Therefore, it is important to use healthy young plants for the more efficient contaminant removal . Sodium bicarbonate is a buffer used to stabilize pH as per requirement in ABR.
Wastewater sampling and analysis
Raw wastewater samples were collected from a residential source of WWRC, WRI, Iran, on a daily basis for performance evaluation. The samples from the inlet and outlet of the reactors was analyzed every 24 h at 10 am for pH, COD, SCOD, BOD5, TSS, TN, PO4-P and MPN of coliform bacteria according to the standard method . In that order, the samples were merely filtered through Whatmann 42 before testing of SCOD and BOD5. The microbial population presented in the inlet and outlet, plant root surface, and Bio-rack surface were examined to determine the total viable count (TVC) using the pour plate technique . The active attached biomass on the surface of Bio-racks was observed by using scanning electron microscope (SEM) as per the standard procedure . Bacteria presented on the support matrix (Bio-racks) were merely isolated on nutrient agar medium and the Gram-negative bacterial identification was done using Mini API (BioMérieux, France).
The morphological characteristics of Phragmatis sp. and Typha sp. in terms of the number of leaves, size of the leaves, number of roots, longest root, dry weight, and ash weight were analyzed every 15 days over a 3 month period throughout the six phases of the HRT evaluation to monitor morphological changes in the plants as per standard practice .
where W1 and W2 are the dry weight of plants at times t1 and t2. Statistical analysis of the data to compare integrated systems on the organic load removal and morphological characteristics of plants growth were done through the variance (ANOVA) and Duncan test using SPSS software . Performance differences were deemed to be significant if p <0.05.
This investigation discusses the possibility application of the Bio-rack wetland system as a post-treatment of anaerobic baffled reactor through single specimens of Phragmites sp. or Typha sp. for DEWATS. In the previous study, the performance of ABR throughout eight-compartment treating domestic wastewater was assessed, simulated, and optimum configuration was determined ,. The ABR toward the treatment of domestic wastewater (750 mg COD/L) clearly showed a stable performance under different hydraulic retention times by having a high compartments number (more than 5). Therefore, the six-compartment ABR was selected in the present study to ensure an effective pre-treatment condition in treating domestic wastewater.
Organic pollutant removal
Since, the constancy of any biological process thoroughly depends on the hydraulic and organic loading rates; the experiments were performed to estimate the satisfactory hydraulic retention time (HRT) of the whole integrated process of ABR followed by Bio-rack system using Phragmites sp. (ABR-BRSUP) and Typha sp. (ABR-BRSUT).
Organic pollutant removal with five days repetition through the integrated systems
21.85 × 1.96
21.63 × 1.90
27.71 × 2.60
27.21 × 2.50
31.95 × 2.2
30.64 × 2.23
37.85 × 3.60
35.93 × 3.56
40.14 × 2.93
37.19 × 2.80
45.21 × 4.20
41.15 × 4.25
Many studies comparing planted systems over unplanted units have been conflicting results regarding the importance of plants in any phytoremediation process ,. In the absence of the rhizomes of the plants, the micro-sites occupied by the wetland unit become anaerobic; lead to a lower rate of impurities elimination. The major advantage associated with the current integrated treatment systems is the presence of the Bio-rack wetland. The Bio-rack process planted with Phragmites sp and Typha sp. examined to offer, respectively, a lower HRT of 9.5 (COD: 77%, SCOD: 79%, BOD5: 84% reduction) and 12.5 (COD: 66%, SCOD: 69%, BOD5: 76% reduction) hours in polishing anaerobic effluent as compared to other relevant literatures ,,. Kaseva  reported average COD removal efficiencies of 56 & 61% at HRT of 1.96 and 1.99 days in the conventional constructed wetlands using Phragmites sp. and Typha sp., respectively. Mbuligwe  was determined the efficiency of conventional constructed wetlands using Typha sp. and Colocasia sp., respectively, by 79 & 75% COD reduction at 1.2 days HRT. The Bio-rack wetland used in this study also showed a higher removal of organic pollutant compared to the duckweed system, in which 54 & 58% COD, 63 & 64% SCOD and 21 & 63% BOD5 reduction could be accomplished at 10 and 15 days HRT, respectively . It can be verified that wetland type, efficient oxygen diffusion, and the high accumulation of the attached bacterial populations on the surface of support matrix are the major factors for high level of removal efficiency in the Bio-rack process.
The Bio-rack wetland with Phragmites sp. exhibits a higher rate of pollutant reduction owing to the extensive root system of the plant which is responsible for desirable rate of the oxygen transfer efficiency, and greater microbial mass contribution in the treatment unit. However, there was a little difference in the removal of organic pollutant at longer retention times during the operation of both treatment processes. The visual observation showed that the Phragmites sp. tends to develop a wonderfully root system which occupies thoroughly over the depth of the treatment unit. Typha sp. appears to have a shallower root system.
Dissolve oxygen silhouette in the reactor
Summary of effluents characteristic with five days repetition from two integrated treatment systems
ABR-BRSUP(overall HRT of 21 hours)
ABR-BRSUT(overall HRT of 27 hours)
Outlet at ABR
Outlet at BRSUP
Outlet at ABR
Outlet at BRSUT
7.45 × 0.09
7.10 × 0.05
7.19 × 0.04
7.50 × 0.10
7.15 × 0.06
7.29 × 0.05
0.16 × 0.05
3.2 × 0.14
0.18 × 0.06
2.6 × 0.20
736 × 51.28
420.4 × 30.96
95.2 × 2.28
713 × 21.40
290 × 17.04
97.4 × 1.52
515 × 42.51
256 × 25.26
53.4 × 6.12
473 × 24
173.8 × 26.25
54.4 × 7.85
342 × 24.36
150 × 12.32
23.4 × 3.13
345.6 × 22
110 × 8.12
26.4 × 1.67
523.4 × 48.22
245 × 42.66
61 × 11.71
521 × 47
237.2 × 28.62
71.2 × 7.33
67.97 × 3.88
56.31 × 5.17
14.02 × 0.64
63.45 × 5.72
51.25 × 4.61
14.41 × 0.32
13.65 × 0.65
20.26 × 1.82
10.73 × 1.16
15.30 × 0.43
22.69 × 2.25
13.13 × 1.04
Both integrated systems can also be a viable option to reduce nutrient levels by more than 75% TN and 14% PO4-P. Dissolved oxygen concentration would seem to be more than 2.5 mg/L in the wetland units. Phragmites sp. has a great potential distribution of roots enhanced nutrient uptake by the root segments in their favorable environment. Literature based evaluation confirms that the present processes potentially have a higher nutrient reduction of 40-58% TN compared to the anaerobic baffled reactor as a standalone solution . It would emphasize that the application of the Bio-rack wetlands, as a post treatment of ABR can effectively improve the quality of treated domestic wastewater to be discharged to surface waters in rural areas.
The suspended solids are removed throughout the integrated systems via sedimentation and filtration phenomena. The efficiency of nutrient (N,P) removal can be explained adequately by the nitrification/denitrification of rhizoremediation process and plant uptake route. Nitrogen removal is rather high for both integrated systems. Phosphorus removal is notoriously poor in any constructed wetland practices . The anaerobic systems typically increase the soluble amount of phosphate while can hardly be removed efficiently through the phytoremediation techniques. The greater percentage reduction of phosphorus can be attained by incorporating the advantages of using chemical divalent cations as a result of superior exchange reaction mechanism. Furthermore, the nutrient elimination would be succeeded by frequent harvesting of plants based on climate condition.
The microorganisms create a sort of natural polymer responsible for their adhesion to develop the biofilm and bio-oxidation mechanism . The support matrix (Bio-rack) provides the evidence of enormous TVC concentrations (Figure 4b). TVC concentrations were also found to be high both on the root surface of Phragmites sp. and Typha sp. It should be realized that Phragmites sp. with its extensive root system enhanced bacterial population throughout the Bio-rack unit. In the Bio-rack wetland, the vicinity of the support matrix, stems and roots of the plants are a preferred environment for many micro-organisms to attach and to degrade pollutants in the phytoremediation process.
Correspondingly, the profiling of microflora population on the surface of Bio-racks can show the presence of approximately 12 bacterial strains grown on nutrient agar medium i.e. Acinetobacter lwoffii, Aeromonas sobria, Escherichia coli, Pseudomonas stutzeri, Aeromonas hydrophila, Citrobacter koseri, Acienetobacter johnsonni, Entrobacter intermedius, Alcaligenes faecalis, Pantoea sp., Pseudomonas putida, Acinetobacter baumanni; this could verify the results of previous work . It should be noted that there is a possibility of other microbial population, which could not be detected in a nutrient agar medium.
Plant morphological study
Morphology characteristics of the plants at initial step and after 15 days operation (n = 5)
After 15 days
After 15 days
Number of leaves
6.2 × 1.8
10.4 × 1.14
8.8 × 1.3
12 × 1.6
Size of leaves (mm2)
24.3 × 2.75
26.65 × 2.17
96.02 × 22
140.05 × 20
Number of roots
9.8 × 1.5
28.2 × 5.8
45.4 × 17.52
94.6 × 18.25
Longest root (mm)
12.7 × 1.43
16.42 × 1.05
19.34 × 4.2
22.64 × 5
Dry weight (g/plant)
0.65 × 0.5
1.17 × 0.6
28.39 × 1.7
32.49 × 1.3
Ash weight (g/plant)
0.035 × 0.006
0.114 × 0.05
3.018 × 0.42
3.91 × 0.2
Pre-estimation of capital cost
Pre-estimated capital cost of integrated treatment systems (Q =1m 3 /d, COD <100 mg/L, and BOD 5 < 30 mg/L)
US$/kg BOD5 removed
US$/kg BOD5 removed
It can be summarized that the anaerobic baffled reactor followed by Bio-rack wetland can accomplish high rate organic degradation; however, the application of Phragmites sp. can make the treatment process partially more concise and reliable. Yet, the effluent of this process requires disinfection before discharging into the river. In addition, the effluent can also be soil infiltrated in soak pit, leach fields and mounds or else discharged underground at soil depths.
The studies highlight the performance of an anaerobic baffled reactor followed by Bio-rack wetland planted with Phragmites sp. and Typha sp. for decentralized treatment of domestic wastewater. These processes are characterized by other integrated treatment practices, where conventional wetland systems have provided in case further polishing of anaerobic effluent and in lieu, a support matrix (Bio-rack) is provided to enrich the aerobic bacteria in the form of biofilm within wetland unit. They eliminate possible limitations of ABR and Bio-rack wetland as standalone solutions, respectively, relating to low nutrient elimination and high organic load restriction. The integrated system planted with Phragmites sp. has low space requirement, low capital investment, and most importantly, high degradation of organic pollutants, which was capable of achieving COD, SCOD, and BOD5 removal as high as 87%, 90% and 93%, respectively, at an overall HRT of 21 h. The integrated process using Typha sp. also showed stable and consistent performance in degradation of organic pollutants, where it was possible to remove 86% COD, 89% SCOD, and 92% BOD5 at an overall HRT of 27 h. Both of these integrated processes are effective for nitrogen removal (77-79%) whereas they are less efficient in removing phosphorus (14 - 21%); divalent cation materials can be incorporated. The relative growth rate could make Phragmites (3.92%) a good species for phytoremediation activities than Typha sp. (0.90%). Phragmites sp. has adapted its root system to extend over the depth of the wetland unit, resulting in higher oxygen transfer efficiency through the roots, better nutrient uptake, and larger surface area for aerobic microbial biofilm to adhere and growth compared to Typha sp. This is a principal function of Phragmites sp. that can potentially increase pollutant reduction in the treatment unit (p < 0.05). It can be concluded that present integrated processes (especially by using Phragmites sp.) can be an ideal technology for DEWATS; however, this calls for detail pilot scale and field studies.
The authors wish to thank to the Water Research Institute (WRI)-Water and Wastewater Research Center (WWRC), Tehran, Iran as well as Yeungnam University of KOREA for their valuable assistance in accomplishing this study.
- Massoud MA, Tarhini A, Nasr JA: Decentralized approaches to wastewater treatment and management: applicability in developing countries. Environ Manage 2009, 90: 652–659. 10.1016/j.jenvman.2008.07.001View ArticleGoogle Scholar
- Nasr FA, Doma HS, Nassar HF: Treatment of domestic wastewater using an anaerobic baffled reactor followed by a duckweed pond for agricultural purposes. Environmentalist 2009, 29: 270–279. 10.1007/s10669-008-9188-yView ArticleGoogle Scholar
- Badalians Gholikandi G, Jamshidi S, Valipour A: Application of electrolysis upgrading the operation of anaerobic reactors. Environ Stud 2013, 38: 9–16.Google Scholar
- Yu Y, Lu X, Wu Y: Performance of an anaerobic baffled filter reactor in the treatment of algae-laden water and the contribution of granular sludge. Water 2014, 6: 122–138. 10.3390/w6010122View ArticleGoogle Scholar
- Foxon KM, Pillay S, Lalbahadur T, Rodda N, Holder F, Buckley CA: The anaerobic baffled reactor (ABR): an appropriate technology for on-site sanitation. Water SA 2004, 30: 44–50.Google Scholar
- Wang J, Huang Y, Zhao X: Performance and characteristics of an anaerobic baffled reactor. Bioresour Technol 2004, 93: 205–208. 10.1016/j.biortech.2003.06.004View ArticleGoogle Scholar
- Sarathai Y, Koottatep T, Morel A: Hydraulic characteristics of an anaerobic baffled reactor as onsite wastewater treatment system. J Environ Sci 2010, 22: 1319–1326. 10.1016/S1001-0742(09)60257-6View ArticleGoogle Scholar
- Liu R, Tian Q, Chen J: The developments of anaerobic baffled reactor for wastewater treatment: a review. Afr J Biotechnol 2010, 9: 1535–1542.Google Scholar
- Badalians Gholikandi G, Jamshidi S, Ebrahimzade V: The response of anaerobic baffled reactor in various operational conditions. Int J Wastewater Treat Green Chem 2011, 2: 1–10.Google Scholar
- Badalians Gholikandi G, Jamshidi S, Hazrati H: Optimization of anaerobic baffled reactor (ABR) wastewater treatment system using artificial neural network. Environ Eng Manage. in press.Google Scholar
- Bodkhe SY: A modified anaerobic baffled reactor for municipal wastewater treatment. Environ Manage 2009, 90: 2488–2493. 10.1016/j.jenvman.2009.01.007View ArticleGoogle Scholar
- Feng HJ, Hu LF, Mahmood Q, Qiu CD, Fang CG, Shen DS: Anaerobic domestic wastewater treatment with bamboo carrier anaerobic baffled reactor. Int Biodeterior Biodegrad 2008, 62: 232–238. 10.1016/j.ibiod.2008.01.009View ArticleGoogle Scholar
- Chang JJ, Wu SQ, Dai YR, Liang W, Wu ZB: Treatment performance of integrated vertical-flow constructed wetland plots for domestic wastewater. Ecol Eng 2012, 44: 152–159. 10.1016/j.ecoleng.2012.03.019View ArticleGoogle Scholar
- Kaseva ME: Performance of a sub-surface flow constructed wetland in polishing pre-treated wastewater - a tropical case study. Water Res 2004, 38: 681–687. 10.1016/j.watres.2003.10.041View ArticleGoogle Scholar
- Mbuligwe SE: Comparative effectiveness of engineered wetland systems in the treatment of anaerobically pre-treated domestic wastewater. Ecol Eng 2004, 23: 269–284. 10.1016/j.ecoleng.2004.09.009View ArticleGoogle Scholar
- Singh S, Haberl R, Moog O, Shrestha RR, Shrestha P, Shrestha R: Performance of an anaerobic baffled reactor and hybrid constructed wetland treating high-strength wastewater in Nepal - a model for DEWATS. Ecol Eng 2009, 35: 654–660. 10.1016/j.ecoleng.2008.10.019View ArticleGoogle Scholar
- Landmeyer JE: Introduction to Phytoremediation of Contaminated Groundwater. Springer, New York; 2012.View ArticleGoogle Scholar
- Stottmeister U, Wiebner A, Kuschk P, Kappelmeyer U, Kastner M, Bederski O, Muller RA, Moormann H: Effects of plants and microorganisms in constructed wetlands for wastewater treatment. Biotechnol Adv 2003, 22: 93–117. 10.1016/j.biotechadv.2003.08.010View ArticleGoogle Scholar
- Valipour A, Azizi S, Raman VK, Jamshidi S, Hamnabard N: The comparative evaluation on the performance of two phytoremediation systems for domestic wastewater treatment. Environ Sci Eng. in press.Google Scholar
- Arivoli A, Mohanraj R: Efficacy of Typha angustifolia based vertical flow constructed wetland system in pollutant reduction of domestic wastewater. Int J Environ Sci 2013, 3: 1497–1508.Google Scholar
- Valipour A, Raman VK, Ghole VS: A new approach in wetland systems for domestic wastewater treatment using Phragmites sp. Ecol Eng 2009, 35: 1797–1803. 10.1016/j.ecoleng.2009.08.004View ArticleGoogle Scholar
- Valipour A, Raman VK, Ghole VS: Application of patent bio-rack wetland system using Phragmites sp. for domestic wastewater treatment in the presence of high total dissolved solids (TDS) and heavy metal salts. Environ Sci Eng 2011, 53: 281–288.Google Scholar
- Valipour A, Raman VK, Badalians Gholikandi G: Comparative evaluation on the performance of bio-rack and shallow pond systems for domestic wastewater treatment. Environ Sci Eng 2012, 54: 453–462.Google Scholar
- Wang J, Zhang L, Lu S, Jin X, Gan S: Contaminant removal from low-concentration polluted river water by the Bio-rack wetlands. Environ Sci 2012, 24: 1006–1013. 10.1016/S1001-0742(11)60952-2View ArticleGoogle Scholar
- Wang J, Zhang LY, Lu SY, Gan S, Jin XC: Removal of N and P from river water treated by the bio-rack wetland planted with Thalia dealbata and Acorus calamus Linn . J Jilin Univ (Earth Sci Ed) 2012, 42: 408–414.Google Scholar
- Marchand L, Nsanganwimana F, Oustrière N, Grebenshchykova Z, Lizama-Allende K, Mench M: Copper removal from water using a bio-rack system either unplanted or planted with Phragmites australis , Juncus articulatus and Phalaris arundinacea . Ecol Eng 2014, 64: 291–300. 10.1016/j.ecoleng.2013.12.017View ArticleGoogle Scholar
- Tangahu BV, Abdullah SRS, Basri H, Idris M, Anuar N, Mukhlisin M: A review on heavy metals (As, Pb, and Hg) uptake by plants through phytoremediation. Int J Chem Eng 2011, 2011: 1–31. 10.1155/2011/939161View ArticleGoogle Scholar
- APHA: Standard Methods for the Examination of Water and Wastewater. American Public Health Association, Washington DC; 2005.Google Scholar
- Costley SC, Wallis FM: Bioremediation of heavy metals in a synthetic wastewater using a rotating biological contactor. Water Res 2001, 35: 3715–3723. 10.1016/S0043-1354(01)00072-0View ArticleGoogle Scholar
- Kalra YP: Handbook of Reference Methods for Plant Analysis. CRC Press, Florida; 1998.Google Scholar
- Ge Z, Zhang H, Zhang Y, Yan C, Zhao Y: Purifying synthetic high-strength wastewater by microalgae chlorella vulgaris under various light emitting diode wavelengths and intensities. J Environ Health Sci Eng 2013, 11: 1–10. 10.1186/2052-336X-11-8View ArticleGoogle Scholar
- Vymazal J, Kropfelova L: Wastewater Treatment in Constructed Wetlands with Horizontal Sub-surface Flow. Springer, Dordrecht; 2008.View ArticleGoogle Scholar
- Karathanasis AD, Potter CL, Coyne MS: Vegetation effects on fecal bacteria, BOD, and suspended solid removal in constructed wetlands treating domestic wastewater. Ecol Eng 2003, 20: 157–169. 10.1016/S0925-8574(03)00011-9View ArticleGoogle Scholar
- Marques JJ, Souza RR, Souza CS, Rocha ICC: Attached biomass growth and substrate utilization rate in a moving bed biofilm reactor. Braz J Chem Eng 2008, 25: 665–670. 10.1590/S0104-66322008000400004View ArticleGoogle Scholar
- Lewandowski Z, Beyenal H: Mass transport in heterogeneous biofilms. In Biofilms in Wastewater Treatment: an Interdisciplinary Approach. Edited by: Wuertz S, Bishop P, Wilderer P. IWA Publishing, London; 2003:147–177.Google Scholar
- Hondulas JL: Treatment of Polluted Water Using Wetland Plants in a Floating Habitat. United States Patent: US5337516, Gatlinburg, Tennessee; 1994.Google Scholar
This article is published under license to BioMed Central Ltd. This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/2.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly credited. The Creative Commons Public Domain Dedication waiver (http://creativecommons.org/publicdomain/zero/1.0/) applies to the data made available in this article, unless otherwise stated.